A Data Source is the point of origin at which data is generated. It is needed as a basis to obtain network process values and corresponds to an IoT edge gateway.
In the JUMO smartWARE SCADA application, there is usually always a data source at the beginning, which is called the IoT gateway and corresponds to the main SCADA server. Other external edge gateways such as the JUMO variTRON can be added and are able to buffer data if there is no internet connection.
By adding further data sources, process values can be buffered if the connection to the SCADA server is not available (update, loss of internet connection).
In this part of the application, you can edit your already created Data Source or create a new Data Source, e.g. a "JUMO variTRON 500".
By selecting the "Data Source" button, you can edit a Data Source that was created earlier. A new Data Source is created via the Plus button.
Assign the name of the Data Source in the Basic Configuration. The Description field is optional. The "Group" field shows the Client in which this Data Source was created. The path is generated automatically by the system.
Once you have entered the name, it is necessary to save.
The device ID and password are then generated automatically. This information is required so that the JUMO variTRON can authenticate itself to the JUMO smartWARE SCADA.
You can choose between EdgeGateway (standard: JUMO variTRON) or DataAdapter (expert mode) as the data type. For expert mode, please get in touch with your JUMO contact.
Attached is the data source of the main SCADA server:
Interaction is only possible if the JUMO variTRON has already been set up and is ready for use.
The timestamp indicates when the Data Source was last accessible.
"Send Configuration" is used to transfer changes or new configurations to the JUMO variTRON or the IoT Gateway.
Online: Causes the Data Source to send values outside the set Transmission Intervals. These values, sent outside the transmission interval, are displayed in the interface but not historicized.
Offline: Causes the Data Source to send values within the Interval.
Check the Activated box to enable the Communication Fault function. This can then be used in the Event Definition.
The maximum offline time determines when the Event is to be triggered.
All references to this Data Source are displayed in the References.
The AuditLog is a change log that transparently shows how the object was changed. For some objects, it also shows which target values were set by a specific person. Power users can use the button on the right-hand side to get a detailed view of exactly what has been changed in the configuration.
The AuditLog can be used to quickly trace what happened to the object last. It corresponds to an extract from the Control Operation Archive.